Water tanks on your property
Water tanks are a vital resource on properties in rural areas of Western Australia where scheme drinking water is not available. Water tanks may also be installed for homes in urban areas.
In most cases your water tanks will be filled with rainwater from your roof but in some cases your tanks may be connected to bore water or filled with water from a water carting service.
Following these simple tips and hints about careful collection and storage of water will help you to make sure that water from water tanks on your property is safe to drink and fit for its intended use.
Is rainwater always safe to drink?
Rainwater in rural areas is usually safe to drink unless it has been contaminated or stored improperly.
Rainwater can be contaminated by:
- bird and other small animal droppings (for example lizards, mice, frogs and possums)
- other debris including dead animals and insects containing microscopic organisms
- air pollution from any nearby industrial emissions or heavy road traffic
- industrial or agricultural activities generating dust and pesticide spray drift
- smoke or other emissions from bushfires or wood heaters
- storage in a water tank or pipe work that is not clean.
Simple ways to protect the quality of water in your tank
Regular maintenance of the whole system, from roof to tank to tap, is the key to good water quality for your home.
- Keep roof catchments, including the gutters and down pipes, clean and clear of leaves.
- Remove overhanging branches of trees, shrubs and potential perches for birds such as wires and TV antennas.
- Cover the inlet and overflow of your tank with a mesh to prevent birds, animals and insects from gaining direct access to the water.
- Make sure your tank has a cover to prevent light from reaching the water, as light encourages the growth of bacteria and algae. The cover should have a tightly sealed hatch, to allow access to the tank for cleaning and inspection purposes.
- Each year allow the first good rains to rinse the roof and gutters and run to waste, by using a first flush diversion device. Using a first flush diversion device will prevent the first portion of roof runoff, which is likely to collect contamination, from entering the tank.
- Ensure that guttering and pipework is self-draining, or fitted with drainage points to prevent corrosion and contamination by metal.
- Maintain your leaf trap, as this will reduce the amount of leaves and debris that enters the rainwater tank through the inlet.
Where can I collect rainwater?
Rainwater can be collected from most types of roofs including:
- terracotta tiles
- galvanised iron
- fibreglass sheeting
It is safe to collect rainwater from asbestos or fibro cement roofs. There is no evidence to suggest that asbestos related diseases occur from drinking this rainwater.
Do NOT collect rainwater from a roof that is:
- made from preservative treated wood (copper chrome, creosote or pentachlorophenol)
- coated with bituminous products
- coated with lead based paints (including any gutters).
Do NOT collect rainwater from parts of the roof with:
- a chimney from a wood burner
- discharge pipes from roof-mounted appliances such as evaporative air conditioners or hot water systems
- chemically treated timbers
- lead-based paints or flashings.
Speak to your water tank supplier about identifying materials on your roof that could contaminate your rainwater.
The amount of water required to adequately supply your needs is dependent upon:
- roof area
- rainwater tank size
- the amount of water used in and around your house.
The Perth Residential Water Use Study (external site) and other publications of the Department of Water (external site) provide useful information about the average in-house water use for appliances based on the number of occupants.
Data about rainfall is available from the Bureau of Meteorology (external site).
Using water tanks in urban areas
A reticulated scheme drinking water supply (scheme water) is the safest and most reliable source of drinking water in urban areas in Western Australia.
Rainwater from your roof can contribute to your yearly water needs and help conserve drinking water reserves, when you use rainwater for activities such as:
- watering your garden
- flushing your toilet
- washing your clothes
- washing your car.
If you live in an urban area and you would like to drink rainwater, you should be aware that there might be an increased risk of pollution.
It is also important to protect our reticulated scheme drinking water supply from any risk of contamination through backflow from private water tanks.
To protect the scheme water supply, water tanks that are connected to scheme water must be fitted with an approved backflow prevention device installed by a licensed plumber.
Can I top up my tank?
You may need to top up your tank with water from a commercial water carting company. Before you do, consider these points:
- Is the tanker exclusively used for drinking water?
- Has the water come from a scheme drinking water supply?
- Has the water been treated with at least 1 milligrams per litre of chlorine whilst in transit?
- Does the water carting company follow the Department’s water carting guidelines (external site)?
The answer to each of these questions should be “Yes”.
What about solar hot water systems on my roof?
Solar hot water systems contain heat transfer fluids, corrosion inhibitors (substance that stops the chemical reaction that creates corrosion) and anti-scaling chemicals that can contaminate water in your water tank if they spill or leak.
Do not collect rainwater from parts of the roof with discharge pipes from roof-mounted appliances such as evaporative air conditioners or hot water systems.
When carrying out maintenance on roof-mounted hot water systems, be sure that maintenance personnel:
- follow correct procedures to prevent rainwater contamination for any work conducted on the roof
- disconnect the pipe to the rainwater tank, and only reconnect the pipe once you are certain there is no leakage after maintenance
- contain and dispose of appropriately all heat transfer fluids, corrosion inhibitors and anti-scaling chemicals from solar hot water systems.
Can I fill a rainwater tank with bore water?
Yes, depending on what the water in the water tank is to be used for.
Depending on local characteristics, bore water may be suitable for uses including stock watering, irrigation, flushing toilets and washing clothes or cars.
Bore water should not be used for drinking, bathing, watering edible plants, food preparation or cooking unless it has been properly tested and treated to make it suitable for the intended use.
For more information about bore water, see our Bore water page.
Do I need to disinfect the water in my tank?
Regular disinfection of water in your water tank should not be necessary.
However, if your water is likely to be contaminated you can disinfect it with swimming pool chlorine, in accordance with the table and notes below.
Table: Water tank disinfectant guidelines
||Calcium hypochlorite 60 – 70%
|Sodium hypochlorite 12.5%
||7 grams per 1000 litres
||40 millilitres per 1000 litres
||1 gram per 1000 litres
||4 millilitres per 1000 litres
- Use either granular calcium hypochlorite or liquid sodium hypochlorite. Do not use both at the same time.
- Calculate the amounts of chemical to add based on the volume of water in your tank at the time, not the total capacity of your tank.
- Do not use stabilised chlorine (cyanurate).
- Allow a minimum of 2 hours before drinking.
- Mix the chlorine in a plastic bucket in the open air before adding it to the tank.
- Do not pour water onto chlorine. Always add chlorine to water.
- Always follow the instructions on pool chlorine containers in relation to safe handling and disposal of the product.
Do I need to clean my tank?
Inspect your tank every 2 to 3 years for the accumulation of sediment (sludge) on the tank floor.
The easiest way to remove sludge is by opening the sludge or scour valve located at the bottom of the tank.
Remember that the inside of a tank is a confined space with little ventilation. If you need to clean your tank consider using a professional tank cleaning service.
Should I routinely test water in my water tank?
Routine testing of water in your domestic water tank is not normal practice and in most cases would not be necessary.
If tested, your results should be compared with the guideline values contained in the Australian Drinking Water Guidelines (external site).
Refer to the Department of Health Publication, Standard Drinking Water Assay (external PDF 79KB) for further information.
See also the National Association of Testing Authorities (NATA) (external site) for a current list of registered analytical laboratories.
How do I make sure mosquitoes are not a problem?
Water tanks can become breeding sites for mosquitoes that can cause severe nuisance and carry serious diseases.
In Western Australia, the mosquito most commonly found to breed in water tanks is a proven carrier of Ross River and other mosquito borne viruses.
To prevent mosquitoes from breeding, make sure that:
- Guttering and pipework is self-draining, or fitted with drainage points.
- Water is not allowed to pool under the overflow outlet or tap as these can become mosquito breeding sites.
- All water tanks are completely sealed. Any holes and spaces will allow mosquitoes to enter your tank.
- The inlet and inspection ports have a fine mesh cover to stop mosquitoes and other insects getting into your tank.
- The overflow is also covered with an insect proof cover, such as plastic insect mesh wired around the pipe.
- Insect mesh is no coarser than 12 x 12 meshes per 25 square millimetres.
A useful short term solution to stop mosquito breeding is to add 1½ cups of liquid food grade paraffin oil (in large tanks greater than 10,000 litres) to the water.
When using food grade paraffin oil:
- add a sufficient amount of food grade paraffin oil to produce a thin film over the water surface
- add the food grade paraffin oil at the end of the winter rains
- add more food grade paraffin oil if the tank overflows
- check the tank several times a year as both food grade paraffin oil and water will evaporate over time.
Do I need building approval?
Before purchasing and installing a rainwater tank, check with your local government for building regulations that apply in your area.
Many councils require that a building application is approved before a water tank can be installed.
Can I use my rainwater tank for firefighting?
Your rainwater tank may be the only source of water to fight fires.
The Department of Fire and Emergency Services (DFES) (external site) may have special requirements you have to follow.
What should I do after a bushfire?
Please refer to our rainwater tanks after a bushfire page.
Can I use water in my water tank for crop spraying?
Water that is used to mix crop spraying chemicals should be separated from your drinking water supply.
Do not use any crop spraying mix water or equipment to top up your drinking water. It may contain harmful chemical residues.
What materials should I use for my water tank and pipe work?
Water tanks can be made from a range of materials including:
- galvanised steel
Any part of your water supply system that comes into contact with drinking water should comply with one of the following Australian Standards (external site). This includes tanks, liners, pipes, taps and valves.
- AS 2070, Plastic materials for food contact use
- AS 2179 –1994, Specifications for rainwater goods, accessories and fasteners
- AS 2180 –1986, Metal rainwater goods – selection and installation
- AS 3500.1 –1992, National plumbing and drainage code. Part 1: Water supply
- AS 3855 – 1994, Suitability of plumbing and water distribution systems products for contact with potable water
- AS 4020 – Products for use in contact with water intended for human consumption with regard to their effect on the quality of water
- AS 4130 – Polyethylene (PE) pipes for pressure applications.
If you are not sure, look for the Standards marking on the product or ask your supplier.
Irrigation piping should not be used for drinking water purposes as it may contain and release lead.
- Keep gutters and roofs clean and in good repair.
- Divert the first rainwater run off after a dry period away from the tank.
- Use a leaf trap on the inlet.
- Screen the inlet and overflow for insects/animals.
- Cover and seal the tank to prevent the entry of sunlight, dust, vermin, mosquitoes and other insects.
- Install a tightly fitting hatch cover for cleaning and inspection purposes.
- Make sure all materials in contact with drinking water are Australian Standards approved.
- Separate crop spraying mix water from drinking water supplies at all times.
- Inspect your tank every 2 to 3 years for the accumulation of sediment (sludge) on the tank floor.
- The inside of a tank is a confined space with little ventilation. If you need to clean your tank consider using a professional tank cleaning service.
- Always follow the instructions on pool chlorine containers in relation to safe handling and disposal of the product.
- A reticulated scheme drinking water supply (scheme water) is the safest and most reliable source of drinking water in urban areas in Western Australia.
Environmental Health Directorate
Department of Health WA
PO Box 8172
PERTH BUSINESS CENTRE WA 6849
Telephone: 9388 4999
This publication is provided for education and information purposes only. It is not a substitute for professional medical care. Information about a therapy, service, product or treatment does not imply endorsement and is not intended to replace advice from your healthcare professional. Readers should note that over time currency and completeness of the information may change. All users should seek advice from a qualified healthcare professional for a diagnosis and answers to their medical questions.